Building in a bushfire prone area introduces a number of additional design, specification and construction parameters that cannot be ignored. These additional requirements can add extra costs to a new home, so it is important to note that there is usually more than one option available to designers and builders to meet the requirements of the building regulations and standards.
Equally, building in bushfire prone areas does not mean that traditional building materials such as timber window and door frames are prohibited. To the contrary, timber windows and doors that have been bushfire tested to meet the radiant heat and flame exposure requirements of the Australian Standard AS 1530 are suitable for use in bushfire prone areas.
For example, Stegbar has a range of timber windows and doors that have been tested and satisfy the provisions of AS 1530.8.1 and meet the requirements for bushfire attack level BAL-40.
The Performance Requirement P2.3.4 of Volume Two (Class 1 and 10 Buildings) of the National Construction Code (NCC) requires a Class 1 building (including decks) or a Class 10a building that is constructed in a designated bushfire prone area to be designed and constructed to reduce the risk of ignition from a bushfire, appropriate to:
- The potential for ignition caused by burning embers, radiant heat or flame generated by a bushfire, and
- The intensity of the bushfire attack on the building.
The NCC defines a designated bushfire prone area as land which has been designated under a power of legislation as being subject, or likely to be subject, to bushfires. As a consequence, the process for identifying bushfire prone areas is a matter for each individual state and territory regulator, and while it differs from state to state, it usually involves an approach to the relevant council or reference to a land mapping facility provided by the respective state regulator or agency. The NCC also includes a number of state/territory variations that should be satisfied.
Where an allotment is in a bushfire prone area, the NCC goes on to provide Building Solutions that meet the requirements of P2.3.4. Part 3.7.4 provides two compliance options:
- Complying with Australian Standard AS 3959 (Construction of buildings in bushfire-prone areas), or
- Using an alternate bushfire protection design as an Alternate Solution that meets P2.3.4.
Australian Standard AS 3959
Following option 1 and using the Australian Standard approach, AS 3959 divides bushfire prone areas into six bushfire attack levels (BAL), based on the severity of the building’s potential exposure to ember attack, radiant heat and direct flame contact:
- BAL-LOW – very low risk
- BAL-12.5 – low risk
- BAL-19 -moderate risk
- BAL-29 -high risk
- BAL-40 -very high risk
- BAL-FZ -extreme risk (Flame Zone)
AS 3959 covers the methodology for determining the BAL for an allotment and goes on to provide the construction requirements for each level of BAL, including for floors, roofs, external walls and windows, verandahs and carports.
By complying with the construction requirements for the respective BAL classification, a new home will meet the requirements of the NCC.